The ONE PLUSTM PEXa cross-linked polyethylene pressure pipe is intended for the construction and repair of internal networks of cold, hot water supply, underfloor heating (operation classes 1, 2, 4 according to GOST 32415-2013).
It is allowed to use pipes for non-category technological pipelines transporting liquid media that are non-aggressive to the pipe material.
ONE PLUSTM PEXa pipe is made of Lutene-H XL1800 material manufactured by LG CHEM, LTD. Lutene-H XL1800 is an ideal material for extrusion of pipes for water supply, heating, underfloor heating, it has long-term cracking resistance, good mechanical characteristics.
The optimal combination of strength and flexibility, good "molecular memory", the ability to extinguish water shocks, withstand freeze-thaw cycles. The low cost of the ONE PLUSTM PEXa pipe is an excellent choice for installing a "warm floor", heating open areas and staircases, stadiums, swimming pools, heating the soil in greenhouses, hotbeds, winter gardens and greenhouses
Lutene-H XL1800 pipes have been tested by the Independent Testing Institute Bodycote Polymer.
Advantages of PEXa ONE PLUSTM pipes:
|Indicator name||ONE PLUSTM PEXa|
|Outside diameter, mm||16||20|
|Inner diameter, mm||12||16|
|Толщина стенки, мм||2,0||2,0|
|Coil length, m||200/100||100|
|Standard Dimension Ratio SDR||8||10|
|Weight 1 r.m. pipes, g||82||131|
|The volume of liquid in 1 r.m. pipes, l||0,113||0,201|
|Emergency temperature (no more than 100 hours)||95ºС|
|Maximum working pressure
1, 2 classes
|Maximum working pressure at temperature 20ºС||1,25 MPa|
|Linear thermal expansion coefficient||(1,2÷1,4х10-4) К-1|
|ИChanging the length of the pipe after heating at a temperature 120ºС within 60 minutes||less 3%|
|Equivalent grain roughness coefficient||0,007|
|Coefficient of thermal conductivity||0,4 W/м·К|
|Способ сшивки полиэтилена||Пероксидный|
|Cross-linking degree, not less||70%|
|Warranty period, years||10|
|Service life subject to the rules of installation and operation, years||
Table of characteristics of service classes according to GOST 32415-2013
|Service class||Tраб, °C||Time at Тpab, year||Tmax, °C||Time at Tmax, год||Tavar,°C||Time at Tavar, ч||Application area|
|1||60||49||80||1||95||100||Hot water supply (60°С)|
|2||70||49||80||1||95||100||Hot water supplyе (70°С)|
|4||20||2,5||70||2,5||100||100||High temperature floor heating.
Low temperature heating with heating devices
|5||20||14||90||1||100||100||High temperature heating with heating devices|
|XB||20||50||-||-||-||-||Cold water supply|
The table uses the following designations:
Tslave — operating temperature or combination of temperatures of the transported water, determined by the field of application;
Tmax — time-limited maximum operating temperature;
Tавар — аварийная температура, возникающая в аварийных ситуациях при нарушении систем регулирования.
HOW TO USE THE TABLE
The maximum service life of the pipeline for each class of operation is determined by the total operating time of the pipeline at temperatures T slave, T max, T avar and is 50 years.
For example, for class 4, the calculation is as follows: 2.5 years (at 20°C) + 20 years (at 40°C) + 25 years (at 60°C) + 2.5 years (at 100°C) = 50 years
Pipe packing specifications ONE PLUSTM PEXa
|Outside diameter, mm||16||20|
|Coil length, m||200||100|
|Box size (LxWxH), mm||800х800х150||800х800х150|
|Number of boxes on a pallet, pcs||14||14|